I ran the compatibility checker with a wiring configuration and the tool reported that the system may not support full configuration. Can you please let me know if my system configuration is supported?
My thermostat has the following wires: T and T
The boiler control utilizes T & T thermostat terminals, this requires a dry-contact to open/close the control circuit to engage the boiler. Typically boiler controls require only an open and closed contact switch therefore an isolation is used to separate the 24VAC that is returned as a control signal from the ecobee thermostat. This isolation relay acts as the 'required open/closed' contact. We refer this to a dry-contact and is quite normal for various manufacturers to use this method.